Star And Delta Motor Connection Pdf
File Name: star and delta motor connection .zip
Star and Delta Connections are the two types of connections in a 3 — phase circuits.
- Comparison between Star and Delta Connections
- Star Delta Starter – (Y-Δ) Starter Power, Control and Wiring Diagram
- Star Delta Connection Control Circuit Pdf
Comparison between Star and Delta Connections
Premium Membership. Learn from experienced power engineers. Most induction motors are started directly on line, but when very large motors are started that way, they cause a disturbance of voltage on the supply lines due to large starting current surges. To limit the starting current surge, large induction motors are started at reduced voltage and then have full supply voltage reconnected when they run up to near rotated speed.
Two methods used for reduction of starting voltage are: Star delta starting and Auto transformer starting.
This is the reduced voltage starting method. Voltage reduction during star-delta starting is achieved by physically reconfiguring the motor windings as illustrated in the figure below.
During starting the motor windings are connected in star configuration and this reduces the voltage across each winding 3. This also reduces the torque by a factor of three. After a period of time the winding are reconfigured as delta and the motor runs normally.
They are used in an attempt to reduce the start current applied to the motor during start as a means of reducing the disturbances and interference on the electrical supply. The contactors are smaller than the single contactor used in a Direct on Line starter as they are controlling winding currents only.
There are two contactors that are close during run, often referred to as the main contractor and the delta contactor. The third contactor is the star contactor and that only carries star current while the motor is connected in star.
The main circuit breaker serves as the main power supply switch that supplies electricity to the power circuit. In operation, the Main Contactor KM3 and the Star Contactor KM1 are closed initially, and then after a period of time, the star contactor is opened, and then the delta contactor KM2 is closed.
The control of the contactors is by the timer K1T built into the starter. The Star and Delta are electrically interlocked and preferably mechanically interlocked as well. The star contactor serves to initially short the secondary terminal of the motor U2, V2, W2 for the start sequence during the initial run of the motor from standstill.
This provides one third of DOL current to the motor, thus reducing the high inrush current inherent with large capacity motors at startup. Controlling the interchanging star connection and delta connection of an AC induction motor is achieved by means of a star delta or wye delta control circuit. The control circuit consists of push button switches, auxiliary contacts and a timer. This sequence happens in a friction of time. After pushing the ON push button switch, the auxiliary contact of the main contactor coil 2 which is connected in parallel across the ON push button will become NO to NC, thereby providing a latch to hold the main contactor coil activated which eventually maintains the control circuit active even after releasing the ON push button switch.
Now Motor terminal connection change from star to delta connection. Thus, the delta contactor coil cannot be active when the star contactor coil is active, and similarly, the star contactor coil cannot also be active while the delta contactor coil is active. The control circuit above also provides two interrupting contacts to shutdown the motor.
The OFF push button switch break the control circuit and the motor when necessary. The thermal overload contact is a protective device which automatically opens the STOP Control circuit in case when motor overload current is detected by the thermal overload relay, this is to prevent burning of the motor in case of excessive load beyond the rated capacity of the motor is detected by the thermal overload relay.
At some point during starting it is necessary to change from a star connected winding to a delta connected winding. Power and control circuits can be arranged to this in one of two ways — open transition or closed transition. Discuss mention above is called open transition switching because there is an open state between the star state and the delta state. In open transition the power is disconnected from the motor while the winding are reconfigured via external switching.
When a motor is driven by the supply, either at full speed or at part speed, there is a rotating magnetic field in the stator. This field is rotating at line frequency. The flux from the stator field induces a current in the rotor and this in turn results in a rotor magnetic field.
When the motor is disconnected from the supply open transition there is a spinning rotor within the stator and the rotor has a magnetic field. Due to the low impedance of the rotor circuit, the time constant is quite long and the action of the spinning rotor field within the stator is that of a generator which generates voltage at a frequency determined by the speed of the rotor.
Open transition starting is the easiest to implement in terms or cost and circuitry and if the timing of the changeover is good, this method can work well. There is a technique to reduce the magnitude of the switching transients.
This requires the use of a fourth contactor and a set of three resistors. The resistors must be sized such that considerable current is able to flow in the motor windings while they are in circuit. The auxiliary contactor and resistors are connected across the delta contactor.
In operation, just before the star contactor opens, the auxiliary contactor closes resulting in current flow via the resistors into the star connection. Once the star contactor opens, current is able to flow round through the motor windings to the supply via the resistors. These resistors are then shorted by the delta contactor. If the resistance of the resistors is too high, they will not swamp the voltage generated by the motor and will serve no purpose.
This is achieved by introducing resistors to take up the current flow during the winding changeover. A fourth contractor is required to place the resistor in circuit before opening the star contactor and then removing the resistors once the delta contactor is closed. These resistors need to be sized to carry the motor current.
In addition to requiring more switching devices, the control circuit is more complicated due to the need to carry out resistor switching. It is Important the pause between star contactor switch off and Delta contactor switch is on correct. This is because Star contactor must be reliably disconnected before Delta contactor is activated. It is also important that the switch over pause is not too long. The phase currents increase by the same ratio. The line current increases three times its value in star connection.
During transition period of switchover the motor must be free running with little deceleration. This is known as transient current. Only lasting a few milliseconds it causes voltage surges and spikes. Known as a changeover transient. For a star-delta starter there is a possibility to place the overload protection in two positions, in the line or in the windings. Disadvantage: If the overload is set to FLC, then it is not protecting the motor while it is in delta setting is x1.
In the windings means that the overload is placed after the point where the wiring to the contactors are split into main and delta. The overload then always measures the current inside the windings. The star-delta method is usually only applied to low to medium voltage and light starting Torque motors. L start. This starting method only works when the application is light loaded during the start.
If the motor is too heavily loaded, there will not be enough torque to accelerate the motor up to speed before switching over to the delta position. Sir, If we connect Main contactor first instead of Star contactor, what will be the consequences. Thanks a lot sir, this ur article is profitable to me. Thanks sir. We are facing the problem with our FD fan of 55 KW for boiler operation — Delta contactor is being stuccked during normal running of the FD fan.
Thanks so much for the knowledge you impacted online and during your stay at the LEC. Sir there is power connection error between main contactor and delta contactor which will cause tripping of contactor when is shifting from star to delta connection. There is a big mistake an error in the above power circuit of star-delta.
Live Y is connected between V1 and V2 which is wrong. Live Y should be connected between V1 and U2. Live B is connected between W1 and U2 which is wrong. Live B should be connected between W1 and V2. In auto Star-delta starter, when star contractor hold motor running but when delta contractor hold motor not run and contractor hold proper,. Search for:.
Star-delta motor starter explained in details. Introduction to Star-Delta motor starter Most induction motors are started directly on line, but when very large motors are started that way, they cause a disturbance of voltage on the supply lines due to large starting current surges.
Traditionally in many supply regions, there has been a requirement to fit a reduced voltage starter on all motors greater than 5HP 4KW. When the motor is reconnected to the supply, it is reclosing onto an unsynchronized generator and this result in a very high current and torque transient. The magnitude of the transient is dependent on the phase relationship between the generated voltage and the line voltage at the point of closure can be much higher than DOL current and torque and can result in electrical and mechanical damage.
In closed transition the power is maintained to the motor at all time. Related EEP's content with sponsored links. It helps you to shape up your technical skills in your everyday life as an electrical engineer. Jignesh Parmar Jignesh Parmar has completed M. Tech Power System Control , B. E Electrical. Leave a Comment Cancel Reply. Learn from experienced engineers and sharpen up your knowledge. Browse Courses. The content is copyrighted to EEP and may not be reproduced on other websites.
Facebook Linkedin Linkedin Twitter.
Star Delta Starter – (Y-Δ) Starter Power, Control and Wiring Diagram
Plc lab manual 4 part 2 1. View and download windsor chariot 2 ivac 24 avt operating instructions manual online. Star delta wiring diagram in pdf. C fantech installation maintenance wiring diagrams m 7 wiring diagrams standard motors m 3o wiring diagrams 1o wiring diagrams m 3 m 3 high speed delta. Three phase electric power is a common method of alternating current electric power generation transmission and distribution. Assemble the components of the circuit shown in figure 12 on the control board and make the required wiring and connections.
Disadvantages of Star delta starter 1 Star delta starter can only useful to motors where the six motor terminals can be accessed. I received many comments and request for Star Delta circuit diagram.. So this time i want share my simple star delta circuit diagram completed with power and control line circuit. I hope it can be as basic reference for all electrician about star delta starter diagram. A star delta starter is the most commonly used method for the starting of a 3 phase induction boutler.
Star Delta Connection Control Circuit Pdf
From the left you have the main contactor with the pneumatic timer because your main contactor is always energized, in the Middle you have the Delta contactor with a thermal overload for motor protection in case the motor exceeds the ampere rating set on the thermal overload, on the right you have the Star contactor which is the first contactor to be energized with the main contactor then when the timer reaches its time limit the Star contactor de-energizes and the Delta contactor energizes and the Motor is running at full load. This way, the circuit is completed, as a result;. Related Post:. Click image to enlarge. Related Posts:.
Premium Membership. Learn from experienced power engineers. Most induction motors are started directly on line, but when very large motors are started that way, they cause a disturbance of voltage on the supply lines due to large starting current surges. To limit the starting current surge, large induction motors are started at reduced voltage and then have full supply voltage reconnected when they run up to near rotated speed. Two methods used for reduction of starting voltage are: Star delta starting and Auto transformer starting.